100 Micron Automatic Self Cleaning Water Filter Purifier
1. Feature of water filter
Low water consumption
Fine filter degree
Low pressure drop
2. How It Works
The unit consists of two stages of filtration, a coarse pre-filter and a stainless steel fine screen.
The unwanted solids accumulate on the inner surface of the fine screen,
Building up a filter cake, which filters out even finer particles,
Creating a pressure differential. Once the pressure drop reaches a preset level,
A rinse cycle is activated by the factory supplied control system.
The solids are removed from the fine screen using a spot backwashing method, which
Aggressively sucks the dirt off the screen, similar to a vacuum cleaner, and are carried to
The drain via the rinse valve.
The dirt collector rotates, ensuring the entire screen is cleaned
Each cycle. The process takes a matter of seconds, without interruption of system flow.
3. Control method
Filter has differential switch and integrator.
Once the pressure drop reaches a preset level,
A rinse cycle is activated by the PLC controller.
1. Chilling water treating: Such like cooling tower, water supplement system, air conditioning system, heat exchange system.
2. Raw water treating: Such like surface water, lake, sea water, tank water, well to remove grind, sand, algae, organism etc.
3. Cycling industry water: Cooling tower, polishing process water, ion exchange water, spraying process water, heat exchange plant, rolling plant, casting plant etc.
4. Irrigation: Farm, dip field, golf, lawn etc.
5. Recycle water
Single flow rate: 15-900m³ /h
The least working pressure: 2.5bar
The highest working pressure: 10-16bar(optional)
The pressure loss of cleaning: 0.1-0.8bar
The highest temperature of working: 70
The water consumption of self-cleaning one time: 1% of all water flow
Filter precision: 80-500 microns
Cleaning method: Sucking type
Cleaning time: 35-90seconds
Connect method: Flange
Drain diameter: 50-80mm
Install Direction: Vertical and horizontal
Control panel show method: LCD
15-900T/H,Achieve parallel install to achieve big capacity
Min work pressure
Max work pressure
Differential pressure, time and manual
65ºC (reach to 100ºC if required)
Back wash time
Differential pressure in cleaning
Back wash water consumption
Carbon steel with anti-corrosion painting
Multi stainless steel mesh + pvc structure
Cast ion with antir-corrosion painting
|Pipe Diameter||Flow (T/H)||Drain pipe diameter||Min Pressure|
|XLQ -50XT||50mm=2' '||25||50mm||0.25MPa|
|XLQ -125XT||125mm||100||50mm||0.25MPa |
|XLQ -250XT ||250mm||450||80mm||0.25MPa|
1,One check valve must be installed at filter outlet. Return pressure and back water is forbidden, in case of screen out of shape.
2,If system wok pressure over 0.8MPa, should install break valve at drain pipe to reduce impact to screen.
3,Notice motor rotating direction. Shut off power immediately once back rotating (anti-clock wise )occurs. )
4,Installation each part according to arrow direction.
5,Sudden pressure relief at outlet pipe is forbidden. Take normal work pressure 1.3MPa for example,if suddenly open branch valve at outlet, it will occur instant huge different pressure,which damagescreen.
6,Make sure filter used under correct work pressure, capacity.
7,If alarms, open by-pass valve for temporary back washing solutions.
8,Make sure control box have constant power supply. If power off, users can open by-pass valve,close in and outlet valve and control box switch.
1,Keep space for filter install and maintenance.
2,Drainage pipe length not longer than 20m. Avoid more turns off, keep outlet pipe parallel with ground.
1,Close inlet outlet valve before testing. Open by-pass valve. Wash dirties staying in pipes.
2,Open inlet valve gradually. Let water into filter till air comes out from filter house.
3,Check leak at joint part, check in/outlet pressure gauge. Connect power when comes to system pressure.
4,Set up drainage time based on system pressure data.
5,Open outlet valve gradually if testing is normal. Close by-pass valve back to normal filtering.
6,Observe several differential pressure changes and drainage. Finish testing if normal.
Notice in using
Equipment can through into operation directly, as already has trial testing. Users can adjust settings based on actual use. Change relay's program and parameter is forbidden.
1st operation notice
Follow below steps in 1st operation
Check drainage pipe connection. No up-inclined angle.
Check connection tighten or not.
Check control box in a dry environment.
Connect power cord, green light means normal. Make sure electrical parts is dry. Water is forbidden into control box.
Welcome to inquire, We will offer you the best items !