Water Treatment Equipment for Air Conditioning SystemApplication
1.Chilling water treating: such like cooling tower, water supplement system, air conditioning system, heat exchange system.
2.Raw water treating: such like surface water, lake, sea water, tank water, well to remove grind, sand, algae, organism etc.
3.Cycling industry water: cooling tower, polishing process water, ion exchange water, spraying process water, heat exchange plant, rolling plant, casting plant etc.
4.Irrigation: farm, dip field, golf, lawn etc.
Fisrt,the water enters into the coarse strainer(witch is in order to prevent fine strainer).Then water enters into the fine strainer,
Impurities will accumulate in the internal of fine strainer,When the pressure differential between water inlet and outlet reaches to
pre-setting value,the motor will wrk automatic.The motor will drive coupling rod rotating and in vertical direction.The sucking nozzle will suck the impurities from the internal surface of fine strainer,Last the impurities will be drained by automatic drain valve.The system's water do not need stop in cleaning process.
Control system of sucking type filter is PLC program developed by our company.There are pressure differential control and time set control .So it will clean automatic whether which process reaches to corresponding value.what's more, operator can select continuous cleaning operation.When the equipment has something wrong,it will send the alert information.Parameter
|Model No||Pipe Diameter||Flow (T/H)||Drain pipe diameter||Min Pressure|
|XLQ -50XT||50mm=2' '||25||50mm||0.25MPa|
|XLQ -125XT||125mm||100||50mm||0.25MPa |
|XLQ -250XT ||250mm||450||80mm||0.25MPa|
|Max Water Temperature||70 centigrade|
(Reach 100 centigrade in special requirements)
|Max pressure||10bar, 16bar (Optional)|
|Control method||Pressure differential control, time control and manual control|
|Filter flow||15-1000 CMB/Hour. If customer need higher flow, we suggest using many automatic sucking type filter parallel.|
|Backwash Time||60-120 seconds|
|Backwash Water Consumption||About 500 kg|
|Power||380.50Hz, 3 phase, Controller 220V|
|Power of Motor||Suction type 0.37Kw|
|Motor||14-20 round every minute|
|Filter chamber material||Resin covering carbon steel or stainless steel|
|Filter strainer||stainless steel (weave, stintering, wedges)|
1.One check valve must be installed at filter outlet. Return pressure and back water is forbidden, in case of screen out of shape.
2.If system wok pressure over 0.8MPa, should install break valve at drain pipe
to reduce impact to screen.
3.Notice motor rotating direction. Shut off power immediately once back rotating (anti-clock wise ) occurs. )
4.Installation each part according to arrow direction.
5.Sudden pressure relief at outlet pipe is forbidden. Take normal work pressure 1.3MPa for example, if suddenly open branch valve at outlet, it will occur instant huge different pressure, which damage screen.
6.Make sure filter used under correct work pressure, capacity.
7.If alarms, open by-pass valve for temporary back washing solutions.
8.Make sure control box have constant power supply. If power off, users can open by-pass valve, close in and outlet valve and control box switch.
Do you have certificates?
Yes , we have ISO / CE certificate and certificate of patent
Do you have design team?
We have a professional design team provide drawings, we wait for your confirmation and production
Can you guarantee delivery time ?
Timely transport, ensure the delivery time
Are you maufacturer ?
Yes, we are the professional water treatment equipment manufacturer in china Contact me, you will get more than that you see !