Iron Removal Filter Water Treatment Plant for Removal of Iron and Manganese
|FOB Price:||Get Latest Price|
|Min. Order:||1 Piece|
|Production Capacity:||3, 000 PCS/Year|
|Payment Terms:||L/C, T/T, D/P, Western Union, Paypal|
- Method: Physical Treatment
- Centrifuge Installation: Horizontal
- Motive Force: Electric Power
- Performance: Water Descaling Machine
- Filtration Speed: 6-8 M3 / H
- Backwashing Compressed Air Quantity: 18 to 25 L/M2. S
- Trademark: peide
- Specification: ISO9001: 2008
- Usage: Industrial, Home, Agriculture
- Style: Vertical
- Usages: Environmental Protection, Water Filter
- Certification: SGS, ISO
- Working Temperature: Room Temperature Stress at Work
- Filter Material Height: 1000-1200 - mm
- Transport Package: Woodencase
- Origin: China
1. Detailed introduction
The manganese sand filter also known as remove the manganses filter.
It is mainly used to remove the iron manganese ion
In the water. Iron and manganese in groundwater in almost at the same time.
If the water with iron, affect the taste of water. Such as papermaking, textile, printing and dyeing,
Leather delicate production water, will seriously affect the product quality.
If long drink water containing high iron manganese content will seriously affect the physical health.
In addition to the method of fe mn water Excessive amounts of iron and manganese under
The action of water is generally used in the oxidation of the dissolved state Of bivalent iron
Or bivalent manganese oxide respectively into insoluble ferric iron or quadrivalence mn compounds.
Using the Adsorption of manganese sand filter manganese iron in addition to the filter can be removed.
Chemical reaction is as follows:
2. Oxidation method
1, Jet aeration, commonly used in flow is small, the project of iron manganese content is not high,
The advantage is less cost.
2, nicole, pump and jet principle, mainly by nicole, pump circulation, inhaled air oxidation.
3, aeration tower, commonly used in large flow, high content of iron and manganese in the project,
The fan of oxygen in the Tower and water can fully contact,
The tower fill polyhedral hollow ball, increasing the specific surface area of water.
4, blast aeration, generally in large flow, such as tap water, iron and manganese content is high,
The cost is high, the running Cost is high.
3. Manganese sand filter production structure
Generally have carbon steel or stainless steel 304, or natural rubber lining anticorrosion
Coating epoxy resin, water, water
Distribution system has a hanging basket cloth cloth have dome plate under water, water,
Stainless steel tubular cloth water
Flat cloth, cloth type water cap with ABS mushrooms and wire cylinder cloth water,
Including water and tubular cloth, cloth
Underwater dome board have a cushion, with great pebbles or composition of quartz sand,
This basically is their gap is big,
Resistance, easy to collect water and backwashing.
4. Manganese sand filter technology parameters<o: P>
1, filtration speed: 6-8 m3 / h
2, working temperature: Room temperature stress at work
3, backwashing compressed air quantity: 18 to 25 l/m2. S
4, filter material height: 1000-1200 - mm
5, backwashing strength: 12 to 15 l/m2. S. Back flush time: 4 to 6 minutes
|Inlet & outlet Diameter DN(MM)||( 100 )||200||200||200||200||200|
|Drainage DN(MM)||( 80 )||100||100||100||100||100|
|Flow rate ( M3/H )||15-50||30-100||45-150||60-200||75-250||90-300|
|Maximum pressure ( MPa )||0.6 ( 1.0 )||0.6 ( 1.0 )||0.6 ( 1.0 )||0.6 ( 1.0 )||0.6 ( 1.0 )||0.6 ( 1.0 )|
|filter area ( M2 )||1.13||2.26||3.39||4.52||5.65||6.78|
|total length ( MM )||( 1320 )||2640||3960||5280||6600||1920|
|Quartz sand ( KG )||860||1720||2580||3440||4300||5160|
|Drain valve interface||4 "× 3 "||4 "× 3 "||4 "× 3 "||4 "× 3 "||4 "× 3 "||4 "× 3 "|
WELCOME TO INQUIRE, WE WILL OFFER YOU THE BEST ITEMS !