0.3-20 T/H Automatic Water Softener for Hard Water
|FOB Price:||Get Latest Price|
|Min. Order:||1 Piece|
|Payment Terms:||L/C, T/T, D/P, Western Union, Paypal|
- Model NO.: FLECK
- Certification: SGS, ISO
- Water Pressure: 0.18-0.6MPa
- Control Method: Time or Flow
- Water Flow: 0.3-20 T/H
- Transport Package: Wooden Case
- Origin: China
- Installation: Wall Mounted
- Inlet Mode: Pipeline
- Operation Method: Manual/Automatic
- Working Electric: 220V/50Hz
- Trademark: peide
- Specification: ISO 9001
0.3-20 T/H Automatic Water Softener for hard water
In the water softening process, water is passed through a bed of sulfonated styrene-divynalbenzene spherical resin beads (about 1 mm in diameter). The exchange sites created on the beads by the sulfonation process are then saturated with sodium ions by passing a brine solution through the resin.
The ion exchange "softening" process takes place when the hardness ions, and Mg2+ and Ca2+ attach themselves to the resin beads causing the sodium ions on the resin beads to be released into the water.
Using an Ion Exchange Column (R = Ion Exchange Resin Site)
When the resin becomes saturated with calcium and magnesium, it is regenerated by passing an NaCl brine solution through the resin. The high concentration of sodium ions in the brine causes the reaction to be reversed with sodium replacing the calcium and magnesium ions which are then discharged into the waste water.
2Na+(aq)+CaR(Solid) -- Ca2+(aq)+Na2R(solid)
All true water softeners work on this principal.
3.Superior corrosion resistance
4.Long life. Automatic Control Valves
Softener equipment applies cation resin for softing raw water,
its main target is to use cation resin to adsorp (main parts of),
encreasing the hardness of raw water.
1. Users can choose manual operation control system for saving cost.
2. If users using for 24 hours can accord to water using time choosing for rebirth
3. Uses can according to water quality requirement: first grade multi-media filter, which can remove mud, rust, colloid and suspension in water. Second grade activated carbon filter, which can remove color, olfactory, biochemistry organic in water and encrease the left oxygen value and pollution in water. Third grade equiped softener equipment.
4. Effluent water capacity achieves the water supply of national low-pressure bioler.
5. Time control- type; flow control- type. In working, apply single-tank, double-tank and multi-tank etc. other varied combination method. When choosing, users can choose as their needs. In operation, it has not only automatic function, but also is manual operation.
Water softener Technicial parameters:
|Hardness of raw water:||<8mmol/L|
|Hardness of effluent water:||≤0.03mmol/L|
|Control method:||time or flow|
System automatic water softener widely used in steam bioler, heating bioler, exchanger, air conditioner, and other systems water softener, also used in hotel, restruant, office, and other life water treatment and food, drinking, wine, washing, textile, chemical, medicine and other industrial softener water treatment.