100-500um PLC Controller Commercial Self-Cleaning Water Filters
|FOB Price:||US $480-5,000 / Piece|
|Min. Order:||1 Piece|
|Min. Order||FOB Price|
|1 Piece||US $480-5,000/ Piece|
|Payment Terms:||L/C, T/T|
- Model NO.: XLQ
- Motive Force: Electric power
- Performance: Efficient Filtration
- Unit Capacity: 15-900t/H,Achieve Parallel Install to Achieve Big
- Max Work Pressure: 1.0MPa,1.6MPa
- Screen: Multi Stainless Steel Mesh + PVC Structure
- Filter Precision: 100-500um
- Control Way: Differential Pressure, Time and Manual
- Trademark: peide
- Origin: China
- Usage: Environmental Protection, Chemical Industry
- Style: Vertical
- Certification: SGS, ISO
- Min Work Pressure: 0.25MPa
- Material: Carbon Steel with Anti-Corrosion Painting
- Install Way: Horizontal and Vertical Installation
- Brand Name: Peide
- Back Wash Time: Back Wash Time
- Specification: ISO 9001
- HS Code: 8421299090
1. How It Works
The unit consists of two stages of filtration, a coarse pre-filter and a stainless steel fine screen.
The unwanted solids accumulate on the inner surface of the fine screen, building up a filter cake,
which filters out even finer particles, creating a pressure differential. Once the pressure drop reaches a preset level, a rinse cycle is activated by the factory supplied control system.
The solids are removed from the fine screen using a spot backwashing method, which aggressively sucks the dirt off the screen, similar to a vacuum cleaner, and are carried to the drain via the rinse valve. The dirt collector rotates, ensuring the entire screen is cleaned each cycle. The process takes a matter of seconds, without interruption of system flow.
Filter has differential switch and integrator. Once the pressure drop reaches a preset level, a rinse cycle is activated by the PLC controller.
Low water consumption
Fine filter degree
Low pressure drop
1.Chilling water treating: such like cooling tower, water supplement system, air conditioning system, heat exchange system.
2.Raw water treating: such like surface water, lake, sea water, tank water, well to remove grind, sand, algae, organism etc.
3.Cycling industry water: cooling tower, polishing process water, ion exchange water, spraying process water, heat exchange plant, rolling plant, casting plant etc.
4.Irrigation: farm, dip field, golf, lawn etc.
15-900T/H,Achieve parallel install to achieve big capacity
Min work pressure
Max work pressure
Differential pressure, time and manual
65ºC (reach to 100ºC if required)
Back wash time
Differential pressure in cleaning
Back wash water consumption
Carbon steel with anti-corrosion painting
Multi stainless steel mesh + pvc structure
Cast iron with anti-corrosion painting
1,One check valve must be installed at filter outlet. Return pressure and back water is forbidden, in case of screen out of shape.
2,If system wok pressure over 0.8MPa, should install break valve at drain pipe to reduce impact to screen.
3,Notice motor rotating direction. Shut off power immediately once back rotating (anti-clock wise )occurs. )
4,Installation each part according to arrow direction.
5,Sudden pressure relief at outlet pipe is forbidden. Take normal work pressure 1.3MPa for example,if suddenly open branch valve at outlet, it will occur instant huge different pressure,which damage screen.
6,Make sure filter used under correct work pressure, capacity.
7,If alarms, open by-pass valve for temporary back washing solutions.
8,Make sure control box have constant power supply. If power off, users can open by-pass valve,close in and outlet valve and control box switch.
Welcome To Inquire, We Will Offer You The Best Items !